Chłodnictwo przemysłowe – Urządzenia chłodnicze SABROE – Urządzenia HeatPAC – recip – kompaktowa amoniakalna pompa ciepła ze sprężarką tłokową . najnowocześniejszy olej do kompresorów, w tym amoniakalnych, [. największą polską firmą dostarczającą freonowe urządzenia chłodnicze dla potrzeb przemysłu, klimatyzacji i pomp ciepła (produkujące sprężarki i agregaty chłodnicze, [. Title in Polish, Analiza funkcjonowania instalacji chłodniczej zasilającej lodowiska systemy chłodnicze, czynnik R, amoniakalne urządzenia chłodnicze.
|Published (Last):||9 April 2011|
|PDF File Size:||3.30 Mb|
|ePub File Size:||3.7 Mb|
|Price:||Free* [*Free Regsitration Required]|
Assign to other user Search user Invite. Additional information Publication languages: Facility manages three outdoor ice rinks, two of them serve as recreational ones and other is speed skating track. Basing on electric energy usage data, maximal electric power demand and total seasonal energy consumption for refrigeration was estimated.
For that the minimal lenght of heat exchanger in water tank was determined.
Polski English Login or register account. It considers maximum heat gains that could occur and as well as in standard conditions basing on weather data for every hour of the year.
Finally the energy and cost savings are calculated as well as the SPBT factor.
Sprężarkowe amoniakalne instalacje chłodnicze – Wytyczne wykonania montażu – Google Books
You have to log in to notify your friend by e-mail Login or register account. The portal can access those files and use them to remember the user’s data, such as their chosen settings screen view, interface language, etc. Operating time is from November to beginnig of March.
High contrast On Off.
Bonca, Zenon ( ). [WorldCat Identities]
The main idea of the design is desuperheating of hot ammonia stream to prepare water for ice resurfacing. The amonikaalne is focused on presenting additional possibilities to reduce energy consumption in the facility.
It allow to create list of users contirbution. Get link to the record. Calculation of heat loads for ice rinks was carried to define cooling demand. You’re going to remove this assignment.
Also the proposition to modify contract with electric energy distributor was made. You can change the active elements on the page buttons and links by pressing a combination of keys:. Assignment does not change access privileges to resource content.
Application of amonia brine cooling systems. The main requirements for ice rinks applications are shown as well as the possibilities to improve energetic efficiency in similar instalations.
By using the Infona portal the user accepts automatic saving and using this information for portal operation purposes. Submitting the report failed.
Change font size You can adjust the font size by pressing a combination of keys: If the error persists, contact the administrator by writing to support infona. Technical progress in the design, chovnicze and safety of ammonia refrigeration systems.
This values are compared to funds for investments determined by the investor. Fields of science No field of science has been suggested yet.
MLEKPOL ZPM RADOM – Tunel chłodniczy
Than heat recovery potential is taken into account and consequently the design of heat recovery system is presented. You can change the cookie settings in your browser. Thesis evaluates the refrigerating system in reference to avalible technologies, legal aspects and environmental impact.